Heat Your Home Office for 8p a Day. Part 1 – Really?
Dylan Winter, boat owner, film maker and blogger, made a youtube video about a year ago showing how four tealights (small candles) can be used to warm up a small well insulated home office. A couple of weeks ago the video went viral, now having ranked up nearly 2.5 millions views. A couple of friends pinged me to see if I could help explain why this apparent miracle in home heating worked. Some pacing around, gazing into space and simulation time later I think I might have an answer.
As humans we tend to spend a lot of time converting energy, rather waiting for energy to be converted for our benefit. Waiting for the kettle to boil, running a car, eating+walking, heating a home, all involve the conversion of energy from one form into another. As we all learnt from an early age, energy can neither be created or destroyed. So, when faced with the concept of using 4 tealights to heat a space the first question to ask is “how much energy is that?”. The wax in a tea light pretty much dissapears after it’s finished burning, all its calorific value has been converted into energy. This equates to about 35W of power that is provided over a 3 to 4 hour period. About 140W (477 BTU/hr for our American cousins) for a morning. Doesn’t seem much but then again that might be because we’re so used to wasting energy, letting it be converted and distributed outside of our needs. We’re used to assuming that a room needs at least 1.5kW (~5000 BTU/hr) to be heated. More an indictment of our almost caveman like home heating technology than anything else.
I’ll delve into why and how this system works so well in later parts of this blog series. For now let’s look at some simulation results of this heating configuration (this time using FloTHERM though admittedly more appropriate for FloVENT).
4 candles (I know there are some of you giggling already, for those that aren’t check out this gem of British comedy) are placed in a bread tin on to which are placed two inverted terracotta flower pots, the larger one with a hole in the bottom (top).
The candles heat the air above the flames, inducing the cold air in from around, over the lip of the bread tin, up into the smaller flower pot, it then passes back down out of that one, up the small gap between inner and outer pots, then out the hole in the top pot.
A complex winding 3D air flow pattern that might be better presented using animated particles:
For this model I placed this flower pot heater on the floor in a small room, with no windows and thick brick walls. The ambient temperature set to 0degC, thus the temperatures predicted in this model will be temperature rises above ambient (well, just about give or take a bit of radiative transfer, more on that key aspect later).
As expected the inner pot gets very hot, the outer one less so as much of the heat is convected up the ‘chimney’ gap between them. Remember this is temperature rise, if this were in a normal room with a 20degC ambient then the touch temperature of the outer pot would be ~37 degC (~100 degF).
What about the room though? After all this is a room heater. The air temperature in the room is raised about 1.5 degC. From an occupied space perspective this isn’t bad at all, especially from 4 tealights.
Why though? If you just had 4 candles sitting on the floor you’d be supplying the same amount of energy to the room. Intuitively you think that wouldn’t be as effective but why? Intuition is a great thing, when it’s correct.
More on the ‘why’ next time.
18th November 2013, Ross-on-Wye
- Dell Precision – Spot on Thermal Design
- Top 10 FloTHERM V10 Features – #11: Odds and Sods
- Top 10 FloTHERM V10 Features – #10: Improved Solar Calculator
- Top 10 FloTHERM V10 Features – #9: Data Center Simulation
- Top 10 FloTHERM V10 Features – #8: Thermostatic Control with Hysteresis
- Top 10 FloTHERM V10 Features – #7: Super-fast Parallel CFD Solver
- Top 10 FloTHERM V10 Features – #6: Integrated Summary Columns
- Top 10 FloTHERM V10 Features – #5: FloSCRIPT
- Top 10 FloTHERM V10 Features – #4: Updated CAD
- Top 10 FloTHERM V10 Features – #3: FEA Interfacing
- September 2014 (4)
- August 2014 (1)
- July 2014 (1)
- June 2014 (4)
- February 2014 (2)
- January 2014 (2)
- December 2013 (2)
- November 2013 (4)
- July 2013 (1)
- May 2013 (2)
- April 2013 (3)
- February 2013 (1)
- January 2013 (2)
- September 2012 (1)
- August 2012 (2)
- July 2012 (3)
- May 2012 (2)
- April 2012 (2)
- February 2012 (1)
- January 2012 (5)
- December 2011 (1)
- November 2011 (1)
- October 2011 (3)
- August 2011 (2)
- June 2011 (3)
- May 2011 (1)
- April 2011 (4)
- March 2011 (1)
- February 2011 (1)
- January 2011 (4)
- December 2010 (1)
- November 2010 (3)
- October 2010 (2)
- August 2010 (2)
- July 2010 (4)
- June 2010 (2)
- May 2010 (4)
- April 2010 (2)
- March 2010 (3)
- February 2010 (3)
- January 2010 (8)
- How much do ‘U-Value’ good thermal insulation? Part I
- Keeping the caveman warm – HVAC blog
- FloVIZ, the free FloTHERM/FloVENT CFD results viewer, try it, it’s free
- ‘Heat Trees’ – taking a leaf out of natures book
- The Most Extreme CFD Model Ever Ever – Explained
- FloTHERM and its new XML neutral file format
- The Most Extreme CFD Model Ever Ever
- So, you want to predict component temperatures do you? Part VII
- December 2009 (2)
- November 2009 (3)
- October 2009 (3)
- September 2009 (3)
- August 2009 (3)
- July 2009 (9)
- At the Speed of Heat
- A Load of HVAC TLAs
- How-to: Invert your thermal model to good effect
- Clogged cooling fins, a cautionary tale
- Invert your thermal model to good effect
- “I work with computers”
- Fractals: Gods Artwork, Part II
- Fractals: Gods Artwork, Part I
- “All models are wrong, but some are useful” Part V
- June 2009 (5)
- May 2009 (3)